Last revised July 17th 2017.
The dimmer can only operate with 0-10V dimmable LED drivers. PWM dimming is not supported.
Input Voltage 100-375VAC, 50-60Hz
Output Voltage 0-10VDC
Operating Temperature -30C to +70C
18 AWG wires (Line, Neutral, DIM+, DIM-)
Wire UL1015 18AWG, stranded
Dimensions – 100mm x 50mm x 25.5mm
Built-in BLE stack
Safety EN 60950-1: 2006+A11:2009+A1:2010+A12:2011 EMC (Art. 3(1)(a)): EN 301 489-1 V1.9.2, EN 301-489-17 V2.2.1, EN 61000-4-3:2006 Spectrum (Art. 3(2)): EN 300 328 V1.9.1
15.247:2012 IC: RSS-210, Issue 8, 2010. RSS-GEN, Issue 3, 2010 ETL: Conforms to UL std. 60950-1. Certified to CSA C22.2 No, 60950-1
The following is the installation process of connecting the BLE Dimmer to its corresponding lighting fixture.
DANGER: RISK OF ELECTRIC SHOCK. DISCONNECT ALL SOURCES OF SUPPLY BEFORE SERVICING.
1. Connect BLACK wire to the LINE input of the LED driver. LINE is also the line of the main AC power.
2. Connect WHITE wire to the NEUTRAL input of the LED driver.
3. Connect the green DIM+ wire to the DIM+ input of the LED driver.
4. Connect the grey DIM- wire to the DIM- input of the LED driver.
5. Position and secure BLE Dimmer near lighting fixture.
Network range can be greatly affected by a number of factors, such as physical obstacles, radio interference and even elevation above ground. In order to achieve the optimal radio coverage, at least one dimmer in a zone has to be within 150 feet within the light of sight from the iCon. Furthermore, the antenna inside the dimmer has less attenuation if a dimmer is at least 5 feet above the ground. In addition, in a multiple dimmer system, the distance between each dimmer within a zone must be within 50 feet line of sight.
In situations in which a zone is out-of-range of the iCon and is also located behind another zone, multiple "dummy" dimmers can be used as "repeaters" to bridge the signal over from the iCon to the out-of-range zone. Connect only AC power to each dimmer and place them approximately 50 feet apart from each other until reaching the desired zone location.
Notice: The unused DIM+ and DIM- wire must be capper properly to avoid short circuiting.
Note: All devices must be at least 5' above the ground. LoS meaning Light of Sight.