Last revised June 1st 2019.
Model Number BOS100
Input 100-375VAC 50/60Hz, 13A
Output 100-375VAC, 13A Max, 4000VA Max.
Bluetooth Low Energy 4.2
Infrared motion sensor range: 360 degrees, 5.5 meter radius
Ultrasonic motion sensor range: 4 meters
Dimensions (Length x Width x Height: 122mm x 128mm x 36mm
FCC ID: QOQBGM113
ETL: Certified to CSA C22.2 No. 60950-1.
UL: Conforms to UL Std. 60950-1.
There are two status lights behind the PIR lens.
Yellow: PIR has detected motion.
Green: Ultrasonic sensor has detected motion.
The sensor works best when mounted between 2 and 2.5 meters high with a direct line of sight to the area of monitoring. It is also best to mount the sensor no more than 15 meters from at least one BLE Dimmer.
The sensor can be mounted on the ceiling or at a corner with the supplied brackets. When mounted at a corner, the bracket provides a 25-degree tilted down angle.
The ceiling bracket has four mounting holes. The two ceiling mounting holes near the center are 35mm apart, whereas the two corner mounting holes are 48mm from the corner. Use the provided wall anchors and M5 screws to secure the bracket.
To mount the sensor on the ceiling, gently push the sensor into the T-shape latch and then slide the sensor towards the middle until you hear a click sound. Feed the wires through the rectangular slot in the middle of the bracket and connect to power. To remove the sensor from the bracket, gently press the lock at the back of the sensor and slide it off the bracket.
To connect the two brackets for corner mounting, slide the cornet bracket into the ceiling bracket as shown below.
To mount the sensor at a corner, connect the two mounting brackets together and gently push the sensor into the T-shape latch at the corner bracket. Slide towards the middle of the sensor until you hear a click sound. Feed the wires through the rectangular slot in the middle of the bracket and connect to power.
A CIRCUIT BREAKER SHALL BE INSTALLED ON THE AC LINES SUPPLYING THE SENSOR. IF YOU ARE NOT FAMILIAR WITH AC ELECTRICAL WIRING, PLEASE ALLOW A LICENSED ELECTRICIAN TO PERFORM THE INSTALLATION.
Wires are separated into two groups. Connect the Line (Black) and Neutral (White) wires to AC power. If the power relay function is being used, then connect the green and grey wires as shown in the diagram below. Otherwise, you can leave the relay wires unconnected.